INSTALLATION OF DG SET
The DG Set is supplied with built in fuel tank, control panel and charged batteries & lube oil in the engine.
At the time of unloading of the DG Set and placing the DG Set on to the foundation, kindly ensure a space of approx. 1000 mm is left on all four sides of the DG Set, so that servicing of DG Set could be done easily.
Before commissioning, the DG Set, has to be connected with body and neutral earthing, along with the necessary cabling as per the details given below.
In case of any query regarding installation kindly do refer "The KOEL(Kirloskar) Manual" provided by the company along with the DG Set or call on 9910495849 or email sales@timkenservices.com.
The earthing strip needs to be connected to the body and the neutral of the DG Set.
Please refer Chart A for earthing and Cable sizes for respective DG Set.
We recommend to use 2 Nos. Body Earthing and 2 Nos. Neutral Earthing for each DG Set.
ANNEXURE – A
INSTALLATION / MATERIAL SELECTION CHART BASED ON DG SET RATING
KVA 
Fuel tank (Ltrs) 
Battery 
Exhaust pipe dia (mm) 
Al armod cable 
Earthing 
15 Single Phase 
65 
1 x 150 
65 
1 R x 2 C x 16 sq. mm 
25 x 3 mm Copper Strip for neutral earthing 25 x 3 mm GI Strip for body earthing 
15 Three Phase 
65 
1 x 150 
65 
1 R x 3.5 C x 10 sq. mm 







20 Single Phase 
65 
1 x 150 
65 
1 R x 2 C x 25 sq. mm 

20 Three Phase 
65 
1 x 150 
65 
1 R x 3.5 C x 16 sq. mm 







25 Single Phase 
65 
1 x 150 
65 
1 R x 2 C x 35 sq. mm 

25 Three Phase 
65 
1 x 150 
65 
1 R x 3.5 C x 16 sq. mm 







30 Single Phase 
65 
1 x 180 
65 
1 R x 2 C x 50 sq. mm 

30 Three Phase 
65 
1 x 180 
65 
1 R x 3.5 C x 16 sq. mm 







35 Single Phase 
65 
1 x 180 
65 
1 R x 2 C x 70 sq. mm 

35 Three Phase 
65 
1 x 180 
65 
1 R x 3.5 C x 16 sq. mm 







40 Single Phase 
100 
1 x 180 
75 
1 R x 2 C x 95 sq. mm 

40 Three Phase 
100 
1 x 180 
75 
1 R x 3.5 C x 25 sq. mm 







45 Single Phase 
100 
1 x 180 
75 
1 R x 2 C x 120 sq. mm 

45 Three Phase 
100 
1 x 180 
75 
1 R x 3.5 C x 25 sq. mm 






25 x 6 mm Copper Strip for neutral earthing 25 x 6 mm GI Strip for body earthing 
50 Single Phase 
100 
1 x 180 
75 
1 R x 2 C x 150 sq. mm 

50 Three Phase 
100 
1 x 180 
75 
1 R x 3.5 C x 35 sq. mm 







55 Single Phase 
100 
1 x 180 
75 
1 R x 2 C x 185 sq. mm 

55 Three Phase 
100 
1 x 180 
75 
1 R x 3.5 C x 35 sq. mm 







62.5 Single Phase 
150 
1 x 180 
100 
1 R x 2 C x 240 sq. mm 

62.5 Three Phase 
150 
1 x 180 
100 
1 R x 3.5 C x 50 sq. mm 







70 Single Phase 
150 
1 x 180 
100 
1 R x 2 C x 240 sq. mm 

70 Three Phase 
150 
1 x 180 
100 
1 R x 3.5 C x 50 sq. mm 







75 Single Phase 
150 
1 x 180 
100 
1 R x 2 C x 240 sq. mm 

75 Three Phase 
150 
1 x 180 
100 
1 R x 3.5 C x 70 sq. mm 







82.5 Single Phase 
150 
1 x 180 
100 
1 R x 2 C x 300 sq. mm 

82.5 Three Phase 
150 
1 x 180 
100 
1 R x 3.5 C x 70 sq. mm 






40 x 6 mm Copper Strip for neutral earthing 40 x 6 mm GI Strip for body earthing 
100 Three Phase 
300 
1 x 180 
125 
1 R x 3.5 C x 95 sq. mm 







125 Three Phase 
300 
1 x 180 
125 
1 R x 3.5 C x 150 sq. mm 







140 Three Phase 
300 
2 x 150 
125 
1 R x 3.5 C x 185 sq. mm 







160 Three Phase 
450 
2 x 150 
125 
1 R x 3.5 C x 240 sq. mm 






50 x 6 mm Copper Strip for neutral earthing 50 x 6 mm GI Strip for body earthing 
180 Three Phase 
450 
2 x 150 
125 
1 R x 3.5 C x 300 sq. mm 







200 Three Phase 
450 
2 x 150 
125 
1 R x 3.5 C x 300 sq. mm 







250 Three Phase 
450 
2 x 150 
125 
1 R x 3.5 C x 400 sq. mm 







320 Three Phase 
450 
2 x 150 
125 
1 R x 3.5 C x 400 sq. mm 







400 Three Phase 
990 
2 x 150 
150 
2 R x 3.5 C x 240 sq. mm 







500 Three Phase 
990 
2 x 150 
2x 125 
3 R x 3.5 C x 240 sq. mm 







600 Three Phase 
990 
2 x 150 
2x 125 
3 R x 3.5 C x 300 sq. mm 







625 Three Phase 
990 
2 x 150 
2x 125 
3 R x 3.5 C x 300 sq. mm 
The commissioning of the DG Set is done trained technician of the company. It advisable to kindly give a days intimation to the company, before the commissioning of DG Set.
Service Dealer Network:
Once the DG Set has been commissioned and in order to have trouble free operation, please do contact the nearest service dealer in your area. It is the responsibility of the service dealer to attend the complaints regarding the DG Set during the warranty period. However the day to day maintenance of the DG Set shall be done by the customer itself.
In case you feel, you could also take an annual maintenance contract (AMC) from the Service Dealer.
SELECT YOUR SERVICE DEALER